This circular displacement ventilation unit is an excellent choice for middle space positioning.
|Front panel||Perforated galvanised steel||Stainless steel (AISI 316L)
|Casing||Galvanised steel||Stainless steel (AISI 316L)
|Pressure measurement pipe||Plastic||–|
|Optinonal top cover||Plastic||–|
|Installation base||Galvanised steel||–|
White (RAL 9003/30% gloss)
|Special colours available|
|Duct cover (1)||DC||Standard lengths
|Installation base (2)||AB||Standard height 100 mm||–|
|Installation base||SB||Standard height 200 mm/
Dimensions = unit size + 60 mm
|High (store) model|
Air is supplied into the space uniformly through the front panel of the unit, generally at a slightly lower temperature than the room air. The supply air flows down to the floor level, before gradually pervading the occupied zone at a low velocity. Finally the convection of warm surfaces causes the air to rise out of the occupied zone. The low velocity flow pattern is circular (360°). The low velocity flow pattern is directed forward.
The non-clogging unit can be easily opened and cleaned.
Halton PRA or Halton PTS/C can be used as an airflow adjustment damper in duct. The safety distance for reliable airflow measurement from the displacement unit is 5 duct dimensions between displacement unit and airflow adjustment damper.
If airflow adjustment damper is installed closer to the displacement unit (minimum distance about 3 duct dimensions), supply air throw pattern is correct, but air flow measurement result will not be accurate.
When installing airflow adjustment damper close to the displacement unit (minimum 3xD), attenuator could be needed between the damper and the displacement unit.
Note: The flow pattern data has been defined for floor installation.
Perform the installation in the following order:
A) Without AS/AB base:
Open diffuser and fix onto floor with screws (not included in delivery)
With AS/AB base:
Fix 3 mounting brackets (2) on to floor and then fix AC/AB base cover (1)
B) After installation of ductwork (7) position the DC duct cover as follows:
Position the fixed half of the DC (5) so that joint of the unit and DC
are in same position. Install brackets (6) into DC
Position and fix the other opening half of the duct cover (4)
The supply flow rate is determined by measuring the differential pressure from the measurement nipple with a manometer. Use a measurement probe thin enough fit into the nipple. Then use tape or another gasket to create a seal in the nipple in order to get an accurate reading.
The flow rate is calculated using the formula below:
The values for k factor for formula
(D = duct diameter)
1. Front panel
2. Detachable service plate
Open the front panel (1) by carefully pulling the spring connections out. Unscrew the service plate (2) screws and remove the plate. If required, the flow equalization nets can be detached.
Wipe the parts with a damp cloth. Do not immerse in water.
Reassemble after cleaning in reverse order.
The Halton Zen Circle displacement ventilation supply unit is made of galvanised steel, polyester-epoxy-painted with a white (RAL 9003) colour.
The unit has a robust maintenance free, non-clogging design.
The unit is comprised of a detachable, perforated front panel, removable service plate,
a plastic internal fixed flow equalisation element, and casing.
The unit has a circular duct connection at the top or bottom depending on the location of the unit.
Mounting brackets are included in the delivery, srcews not.
The unit can be equipped with a duct cover and/or installation base, where required.
Additionally, different colours and surface patterns are available on separate request.
The front panel of the unit is available of 1.5mm thick galvanised steel for demanding spaces.
D = Diameter of duct connection (mm)
125, 160, 200, 250, 315, 400, 500, 630
MA = Material
AS Stainless steel (AISI 316L)
TP = Front panel thickness 1.5 mm
CO = Colour (metallic parts)
SW Signal white (RAL 9003)
X Special colour
TM = Top cover (in the opposite end of duct connection)
F Flat (standard)
BM = Installation
T Ducting from top
B Ducting from bottom
ZT = Tailored product
Y Yes (ETO)
DC Duct cover
AB Standard base
SB High store base
ZCI-200, MA=CS, TP=N, CO=SW, TM=F, BM=0, ZT=N