Aesthetic in design corner model displacement ventilation unit.
|Front panel||Perforated galvanised steel||Stainless steel (AISI 316L)
|Casing||Galvanised steel||Stainless steel (AISI 316L)
|Perforated galvanised steel||–|
|Duct cover||Galvanised steel||–|
|Installation base||Galvanised steel||–|
White (RAL 9003/30% gloss)
|Special colours available|
|Duct cover (1)||DC||Standard lengths
1000 / 1500 /2000 mm
|Installation base (2)||AB||Standard height 100 mm||–|
|Installation base||SB||Standard height 200 mm/
Dimensions =unit size + 60 mm
|High (store) model|
Air is supplied into the space uniformly through the front panel of Halton Zen Corner,
generally at a slightly lower temperature than the room air. The supply airflows down to the floor level, before gradually pervading the occupied zone at a low velocity. Finally the convection of warm surfaces causes the air to rise out of the occupied zone. The low velocity flow pattern is quarter-circular (90° ).
The non-clogging unit can be easily opened and cleaned.
Halton PRA or Halton PTS/C can be used as an airflow adjustment damper in round duct sections. The safety distance for reliable airflow measurement from the displacement unit is 5 duct dimensions between displacement unit and airflow adjustment damper.
If airflow adjustment damper is installed closer to the displacement unit (minimum distance about 3 duct dimensions), supply air throw pattern is correct, but airflow measurement result will not be accurate. When installing airflow adjustment damper close to the displacement unit (minimum 3xD), attenuator could be needed between the damper and the displacement unit.
Note: The flow pattern data has been defined for floor level installation.
Perform the installation the following order:
A) Installation without base:
Fix mounting brackets (4 places) to the displacement ventilation unit (1).
Position the unit (2) against wall and secure with mounting brackets
(included in delivery).
Installation with base:
Fix the base (6) onto the floor and fix the displacement ventilation unit (2)
onto that. Secure with mounting brackets on top (1) (2 places).
B) Fix displacement ventilation unit duct cover frames (4) onto the wall between
the unit and ceiling with screws (3).
C) After installation of the ductwork, install the front plate of the duct cover (5).
D) When multiple sections of duct covesr are used, secure them with screws
(not included in delivery).
If ceiling installation (not recommended) is required, please contact sales.
The supply flow rate for displacement ventilation unit is determined by measuring the differential pressure from the measurement nipple with a manometer. Use a measurement probe thin enough fit into the nipple. Then use tape or another gasket to create a seal in the nipple in order to get an accurate reading.
The flow rate is calculated by using the formula below:
The values for k factor for formula
(D = duct diameter)
1. Front panel
2. Inner panel
Open the front panel (1) by carefully pulling the spring connections out.
Open the inner panel (2) by unscrewing the screws.If required, the flow
equalization plate can be detached.
Wipe the parts with a brush or damp cloth. Do not immerse in water.
After cleaning, reassemble in reverse order.
The Halton Zen Corner displacement ventilation supply unit is made of galvanised steel, polyester-epoxy-painted with a white (RAL 9003) colour.
The unit has a robust maintenance free, non-clogging design.
The unit is comprised of a detachable, perforated front and inner panel, an internal flow equalization plate, and casing.
The unit has a circular duct connection at the top or bottom, depending on the location of the unit.
Mounting brackets are included in the delivery, screws not.
The unit can be equipped with a duct cover and/or installation base, where required.
The front panel of the unit is available of 1.5 mm thick galvanised steel for demanding spaces.
D = Diameter of duct connection (mm)
125,160, 200, 250, 315, 400, 500, 630
MA = Material
AS Stainless steel (AISI 316L)
TP = Front panel thickness 1.5 mm
CO = Colour
SW Signal white (RAL 9003)
X Special colour (RAL xxxx)
ZT = Tailored product
Y Yes (ETO)
DC Duct cover
AB Installation base (standard)
SB Installation base (high, store model)
ZCO-125, MA=CS, TP=N, CO=SW, ZT=N