|Front panel||Steel||TDM/N solid
|Coupling sleeve||Galvanized steel||Gasket|
|Duct gasket||Rubber compound|
White RAL 9010
|Special colours available on request|
TDM/N Solid front panel (without perforation)
TDM/P Perforated front panel
|Control knob||K||Control knob for Halton manual cabin unit|
Air is supplied horizontally into the space through the side slots of the diffuser and induces the room air in the vicinity of the diffuser. The recommended maximum air temperature difference between supply and room air is 10 °C degrees.
Air is supplied horizontally into the space through the side slots and perforated front panel of the diffuser and mixes with room air in the vicinity of the diffuser. The air jet supplied horizontally through the side slots induces room air and mixed supply air. The recommended maximum air temperature difference between supply and room air is 10 °C degrees.
The diffuser can be connected to the Halton cabin unit by using duct between cabin unit outlet and diffuser in order to reach the false ceiling level. Diffuser can be also connected directly in cabin unit outlet. In this case cabin unit outlet has to be female connection. Diffuser can as well be connected directly to the duct or plenum box.
Open the front panel of the diffuser and clean the parts by wiping with a damp cloth. Push the front panel back into place so that the springs lock.