For use as a primary air intake device or can be used as an exhaust air diverter. These are commonly used in Engine/Machine rooms and HVAC equipment rooms for air management.
USM louvres are manufactured for rectangular openings (width B150-1500 mm and height H150-2400 mm, with
1 mm division). Modular contruction for larger sizes is available.
Special flange configurations are available on request.
|Fixed blades||Steel||Painted* or galvanized||Blade material thickness 1.0 mm|
|Fixed blades||Stainless steel EN 1.4404 (AISI316L)|
|Fixed blades||Stainless steel EN 1.4432 (AISI316L)|
|Fixed blades||Aluminium ENAW 5754 / EN 6060||Painted*|
|Frame||Steel||Painted* or galvanized||Frame material thickness 3.0 mm as standard|
|Frame||Stainless steel EN 1.4404 (AISI316L)|
|Frame||Stainless steel EN 1.4432 (AISI316L)|
|Frame||Aluminium ENAW 5754||Painted*|
|Mesh||Galvanized steel||Mesh opening 10 mm|
|Mesh||Stainless steel EN 1.4404 (AISI316L)||Mesh opening 12.7 mm|
* Painted RAL9010, C2 as standard. C2 average service life 5 years. C5-M with average service life of 10 years available as an option.
Air is supplied or extracted through the horizontal blades. The design of the grille prevents rainwater from reaching the ductwork. The slot between the frame and the top blade is sealed, thus preventing rainwater from entering the ductwork from above. Drops of water are collected in the grooves at the front edge of the blades. Water flows to the side grooves, where it drops down.
Traditional outdoor louvre
Rain falling on the vane flows downwards to the front edge of the vane. Drops formed at the edge fall down on the vane below, and upon contact with the vane surface break into small droplets and spray which are easily moved by the air flow through the louvre. Water flowing along the wall onto the louvre penetrates the slot between the frame and the top vane unless the slot has been closed.
USM blade construction
The vanes of the USM louvre are designed to collect the droplets in grooves at the front edge of the vanes. Once the slot between the frame and the top vane has been securely closed, water flowing down the wall will not enter the louvre. The top vane directs the water to the side grooves, along which the which the water flows down past the air flow.