The Halton KVM canopies that are manufactured according to USPHS guidelines. The KVM extraction canopies are used to capture and remove steam and heat resulting e.g. of the industrial dishwashers and bain-maries. The KVM canopies are the choice when grease filtration is not required.
|V||Max 50 mm|
The dimensions presented above are for modular sections only. Larger canopies are assemled using a combination of separate module vane, which makes transportation and on-site handling easier.
|WEIGHTS OF KVM CANOPIES (kg)|
The above table represents an indication of different size of KVM canopies. Height of the canopy is 300 mm.
|Main body||Stainless steel EN 1.4301 (AISI304)||1,25 mm||Option: EN 1.4404 (AISI316L)|
|Light fixture||Painted steel||–||–|
The parts of the KVM canopy are manufactured from polished stainless steel EN 1.4301 (AISI304). The joints on the lower edge of the canopy are fully welded.
Amount, location and sizes of exhaust connections are defined by the customer. Both square and circular connections in various sizes can be done. Connection includes a net hatch.
The galley steam canopies shall be constructed from stainless steel EN 1.4301 (AISI304), material thickness 1,25 mm. The galley canopies shall be supplied complete with outer casing / main body, fluorescent light fitting and exhaust collar with net hatch. The manufacture of canopies shall be controlled by ISO 3834-2:2005, ISO 9001, 14001 and OHSAS 18001 standards. The design of canopies shall follow USPHS guidelines.
Outer casing panels shall be constructed of stainless steel sheet EN 1.4301 (AISI304) with a polished finish. Each joint shall be welded. The joint of the edges shall be fully welded.
The spigot connections for exhaust air shall be constructed from stainless steel EN 1.4301 (AISI304) and shall be supplied with a net hatch.
Each canopy shall be delivered with a fluorescent light fixtures or LED light fixtures providing approx. an average illuminance of 500 lux at the work surfaces of the cooking appliances. The light fixtures shall be suitable for a single-phase 230-VAC power supply and shall be manufactured to be of protection class IP67. The ballast and capacitor shall be located within the light frame. The core electric cables connecting the light fixture to the junction box shall be provided.The light fixture shall be installed on a hinged maintenance hatch, allowing access to the hood roof.
|L < 1250 mm, 2×24 W||720 mm||220 mm|
|L > 1250 mm, < 2000 mm, 2×39 W||1020 mm||220 mm|
|L > 2000 mm, 2×49 W||1620 mm||220 mm|
|L < 1250 mm, 1×28 W||720 mm||175 mm|
|L > 1250 mm, < 2000 mm, 1×42 W||1020 mm||175 mm|
|L > 2000 mm, 1×69 W||1620 mm||175 mm|
Each canopy shall be provided with a maintenance hatch made of stainless steel EN 1.4301 (AISI304) with a shock-resistant plastic window. The heat tolerance of the window shall be up to +115 °C. The hatch shall be easily opened and closed.
(H)=Height of front end
In KVM canopy the front and back ends are same
(SS) Stainless steel EN1.4301
(AS) Stainless steel EN1.4404
(DS)=Diameter of supply connection
(NA) Not Assigned
(DF)=Qty of supply air connections
(DE)=Diameter of exhaust connection
(NA) Not Assigned
(DF)=Qty of exhaust air connections
(QR)=Qty of exhaust connections rectangular
(A) Type SLR
(B) Type LED SLV
(HE) Ceiling condensation removal heating