Smaller in size transfer unit.
|Casing (3)||Galvanised steel||–|
|Front panel (1, 2)||Galvanised steel||–|
|Attenuation material||Mineral wool||–|
|Finishing||Front panels epoxy-painted/
White (RAL 9003/30%)
Air moves to adjoining rooms through the transfer unit due to pressure difference.
The transfer unit attenuates sound and reduces air-borne noise between rooms.
The transfer unit distributes air evenly in different directions.
The transfer unit prevents vision from room to room.
1, 2 Front panels
The transfer unit is installed in an opening made in a wall.
The dimensions for installation hole are:
|Installation hole||(L2+5) x 95 mm||(L2+5) x (30… 60) mm|
|Wall thickness||80…150 mm||unlimited|
Detach the front panels for cleaning.
Clean the unit using a vacuum cleaner.
Wipe the front panels with a damp cloth instead of immersing into water.
The transfer unit has a sound attenuating casing and two exposed front panels with side openings.
The transfer unit is manufactured from galvanised steel with a white (RAL 9003) colour.
Sound attenuation material is coated mineral wool.
The depth of the casing is adjustable according to the thickness of the wall.
The transfer unit can have two exposed front panels without casing.
S = Construction
N Standard (front panels + casing)
B Front panels without casing
W = Width (mm)
300, 400, 500, 600, 700, 800, 900, 1000
H = Height (mm)
CO = Colour
SW Signal white (RAL 9003)
X Special colour (RAL xxxx)
ZT = Tailored product
Y Yes (ETO)
TVA/N-600-100, CO=SW, ZT=N