UL/ULC Listed – The KVS kiosk ventilation system is developed for kiosk-type food court operations and nontraditional sites. The KVS can serve various combinations of commercial type electric cooking appliances. The KVS can be used where NFPA96 ductwork cannot be installed. Tested and listed in accordance with UL710B. For use with electrical equipment only.
The ductless Kiosk Ventilation System shall be a Halton Model KVS recirculating system, UL/ULC listed. The system shall have a listed exhaust filter hood, complete with Halton stainless steel GFIII UL/ULC listed filters, mounted 6’-2” (1880mm) from floor level. The filtration tower shall include filter’s module, fan and motor, fire protection, odor control system and electrical cabinet.
The filtered, clean air shall be discharged back into the cooking area (or ducted outdoors), partially through the air wall vents and/ or through the air register mounted on the top of the unit. The assembly shall be stainless steel construction, with all exposed welds ground and polished to the original finish of metal. The system shall be fully self-supported, pre-piped and wire for a fully automated operation, factory tested and balanced. The installation shall comply with NFPA 96, Chatper 10.
For inquiries, request a quotation or ask our specialists. We are here for you.
Our team looks forward to hearing from you. Please fill in the form. We’ll be in touch with you shortly.