Circular and compact in design for free installation with adjustable airflow.
|Nozzles||Polypropylene (PP)|| Colour alternatives:
White, Grey and Black
|Attenuation material||Polyester fibre|
|Coupling sleeve||Galvanised steel|
|Finishing||Painted, white (RAL 9003)||Special colours available|
Air is supplied either horizontally into the space or alternatively vertically through the adjustable nozzles in the front panel of the diffuser and mixed with the room air outside of the diffuser. Horizontal swirl jet and different air patterns can also achieved by adjusting the nozzles.
The recommended maximum air temperature difference between supply and room air is 10 0C.
The maximum recommended temperature for plastic material is 60 0C.
1. Front panel with nozzles
The terminal unit is connected directly to the duct by screwing or riveting. Adjust the flow pattern in the desired direction by individually rotating each nozzle in order to meet the required specification.
It is recommended that the minimum safety distance before the terminal unit is 3xD.
1. Front panel with nozzles
2. Measurement and adjustment module
The supply airflow is determined using the measurement and adjustment module MSM.
Detach the plug in the plenum and connect the manometer. Measure the differential pressure using the connected manometer. The supply airflow rate is calculated using the formula below.
Adjust the supply airflow rate by rotating the control spindle until the desired setting is achieved.
Lock the damper position with the screw.
Reassemble the tubes and spindle into the plenum and reinstall the plug.
The k factors for installations with different safety distances
(D = duct diameter)
|NS||> 8xD||min. 3xD|
Detach the cover plug and open the front panel of the diffuser. By pressing the stoppers each nozzle can easily be removed through the front panel. Wipe the nozzles and front panel with damp cloth. The nozzles are relpaced by pushing into the front panel.
Remove the measurement and adjustment module by gently pulling the shaft (not the control spindle or measurement tubes!). Wipe the parts with damp cloth, instead of immersing in water.
Reassembly the measurement and adjustment module by pushing the shaft back into place until yhe unit meets the stopper.
Reinstall the front panel back into place.
The diffuser and plenum is made of painted steel with a white (RAL 9003) standard colour. The front panel of the diffuser is equipped with plastic nozzles, which have two-slot construction in order to ensure effective mixing of supply air. Nozzles are individually adjustable to provide high flexibility for the adjustment of the throw pattern.
The diffuser is integrated to a balancing plenum equipped with a measurement and adjustment module.
The diffuser has detachable front panel in order to provide access to the measurement and balancing module in the plenum and to the duct.
The plenum has detachable a spigot equipped with integral gasket for airtight duct connection.
D = Diameter of duct Connection
100, 125, 160, 200, 250
CO = Colour
SW White RAL 9003
X Special colour
Colour for nozzles is not selectable.
ZT = Tailored product
Y Yes (ETO)
DRV-100, CO=SW, ZT =N